Contour Chemical Plant Mitre Bend Repair
14” diameter bend
2 barg operating pressure
30C operating temperature
9.53 original wall thickness
3.2 mm of wall thickness remaining.
A repair was designed by the Clock Spring Technical Centre using ISO 24817. The pipe was cleaned using water and sand blasting. 15 layers of Clock Spring Contour were applied over the pipe.
3 days on-site using Clock Spring Contour trained and approved technicians.
Area to be repaired after sand blasting.
First 4 layers installed and left to cure.
Have a question or need more information? Give us a call or fill in the form, and one of our representatives will reach out to you soon.
Fields with * are required